CLIENT: Prelchim SRL
Network strengthening for the connection of the RDS&RCS user from circuit 2 PTA SIRINEASA 2.
The foundations for the designed pillars 50 (SC 10005) and 70 (SC 10002) were executed
The straightening of the existing pillars no. 48 (VL 014769), 49 (VL015600) and the replacement of designed pillars no. 50 (VL015596/DO310244), 51 (VL015594/DO3102450), 52 (VL015601/DO310247), 53 (VL015588/DO310247), 75 (VL015595 /DO310248).
A new circuit was installed on the circus route. 2 conductor T2X95OL-AL+3X95+2X25mmp in length of 260m. Arrow stretching and insulation resistance measurements were performed. The connections to the earth sockets have been made. The new circuit was energized.
Consumers and public lighting were taken over and the balanced loading of the phases was checked. The disassembly of circuit 2 PTA Sirineasa 2 AL 50 rope conductors and supporting elements was carried out.
TOPO elevations were made and GIS plates were mounted on the building elements.
Duration of work: The project was carried out between 16.02.2022-17.02.2022.
Team: The team consisted of 5 electricians.
Location: Sirineasa, Vâlcea County
Obstacles: The degree of complexity of the work was of medium level, the access of the machines being more difficult.
Work completed: 17.02.2022
Benefits for the community: ensuring the power supply of the telecommunications hub, improving the voltage level for consumers fed from circ 2